I would like to pass on our thanks to yourself and your team for their assistance over the last few weeks with the gas compressor. The change out of the NDE bearings showed them to be suffering some damage. It was impressive to see it identified through the routines, your advise and assistance in agreeing the best course of action was appreciated, I’m sure we will be able to draw on this experience in the future.
Thanks for the excellent reports, we’ll get on with the checks straight away.
Unit transformer 12 had only half of its cooling system in operation due to, it turns out, a major air lock.
Manufacturers Brush have confirmed that in the event of Unit Tx 11 circuit tripping, & Unit Tx 12 picking up its load, even with forced air cooling via integral fans, Transformer 12 could not have been operated safely with only half of the cooling system in operation.
Repair work has been carried out on both transformers & the thermal images from our own camera show the transformers to be operating correctly.
This could have had cost implications into the hundreds of thousands of pounds in asset damage & loss of operational revenue.
I will never forget the excellent help we got from you and your team in Egypt !